||Title:||BUILDING (STANDARDS OF SANITARY FITMENTS, PLUMBING, DRAINAGE WORKS AND LATRINES) REGULATIONS||Gazette Number:|
|Regulation:||38||Heading:||Eaves gutters||Version Date:||30/06/1997|
(1) Eaves gutters shall be-
(2) The size of eaves gutters shall be calculated at the rate of 700 mm2 of cross sectional area of gutter to every 7 m2 of horizontal roofed-over surface. (L.N. 294 of 1976)
(a) made of cast iron or other approved material;
(b) fixed at a gradient not less than 1 in 100; and
(c) properly connected to rain water pipes.